Installation and Maintenance Instructions
according to Regulation DIN 82079
Information about the Manufacturer
Giebel FilTec GmbH
Polypropylene, PVC, EPDM
No ingredients that must be named according to Regulation (EC) No. 1907/2006.
Structure and Materials
|Housing material||Polyprpylene / PVC|
|IBC connection||NW 150 & NW 225|
|Adsorber connection||BSP G ¾“ female|
|Operating temperature||-40°C - +80°C|
|Total weight [kg]||0,6||11|
Installation and Commissioning
1. Screw the IBC cover onto the IBC.
2. Screw the adsorber into the upper thread.
1. Unscrew the adsorber.
2. Remove the IBC cover by unscrewing it.
3. Check seal for damage. Replace with new if necessary.
4. Screw the IBC cover onto the new IBC.
5. Screw the adsorber into the IBC cover again. For this purpose, slightly oil the thread beforehand.
Risik and Hazard Analysis
1. Humid Air flows into the IBC
Moist air can flow into the IBC at the porous points. The seal should be checked according to the maintenance schedule.
2. The IBC Cover is damaged
When selecting the IBC cover, the ambient and operating conditions should be taken into account. An aggressive environment or liquid in the IBC may damage the IBC cover.
The ambient and operating temperatures should not exceed or fall below the specified range, otherwise the IBC cover may be damaged.
Incorrect or improper handling can damage the IBC cover. The recommended assembly must be observed.
1. Check Seal for Wear
|Check||The seal installed in the IBC lid must be checked for perfect condition. For this purpose the seal should be examined for brittleness.|
|Measures||If damage is present, the IBC lid should be replaced.|
2. Visual Inspection of the IBC Cover
|Check||The IBC lid must be visually inspected for damage. Damage can occur due to various environmental or operating conditions or improper handling.|
|Measures||If the IBC lid shows signs of damage, it should be replaced to ensure that the adsorber is fully functional.|
3. Replacement of the Wearing Parts
|Check||The wearing parts, especially the seal, must be checked with regard to their condition.|
|Cycle||Every two years|
|Measures||Regardless of the result of the test, it is recommended to replace the wearing parts to ensure smooth operation.|